1.Position the CombiPump in the required area and using the diagram below or the supplied template. Decide where the inlet position will be made.
2.Drill the desired inlet hole into the holding tank dependant on the model and fit the deflector supplied. NB See information below for minimum inlet heights
3. Inlet MUST NOT be drilled in hatched areas or anywhere on Side D. This will damage the pump and void any warranty and result in breakdown of the unit.
Minimum Inlet heights
The 70mm should be measured from the bottom of the cabinet upwards.
Pump activation 40mm
The 190mm should be measured from the bottom of the cabinet upwards.
Pump activation 75mm
Dimensions: Height 470mm, Width 250mm, Depth 450mm.
Inlet 1.5 “ with supplied Deflector Outlet 3/4 “ BSP to 15mm or 22mm pipe.
Airgap required at top of run.
Run must be vertical with no bends.
Outlet pipe size: 15mm
Head: 9 metre
Capacity: 160 litres/per minute
Maximum temperature 96° C
Operating temperature 85° C
Current 2.45 Amps FLC
Motor output 0.4kW
Pump speed 2800 RPM
Output flows 160 litres per minute @ 9m head
BMS high water Available on request
Capacity 15 litres
Dimensions CB4 & CB7 H:445mm W:260mm D:420mm
Inlet water connection 1 ½” connection (fittings supplied)
Outlet water connection 3/4” BSP PVC
Call today on 01279 780250
Tel: 01279 780250